Ran across a weird phenomena. I have two Waterfurnace 7 Series units (3T and 4T). Both have energy monitoring and both have electric backup heat packs installed. I happened to look at the energy usage the other day and the fans in both units show 38W being used at all times that the units are running regardless of actual fan speed; 0W being shown when the units are off. This seemingly implies that the fan CT is doing something. When the units were first installed and put into service (Oct 2019), the fan wattage for both units would ramp up and down as fan speed ramped up and down with compressor speed. 38W was probably the fan speed 3 energy use (if I remember correctly). In Dec 2019, electric heat packs were installed in both units (delayed due to electric service and load panel upgrades needed). I can't remember if the fan energy use ramped up and down following that or not. But, I bring it up, because I see from the electric heat pack installation instructions, that the CT for the fan is supposed to be shifted from the fan brown wire (factory installed location) to the purple wire attached to the elec heat pack on 15kW and 20kW elec heat units. My 4T unit has a 15kW heat pack but my 3T unit has a 10kW heat pack. Both units have the fan CT donut on the brown wire from the factory. At a minimum, it would seem like the fan CT on the 4T needs to get moved to properly report energy usage. But per the heat pack instructions, that doesn't seem applicable for the 10kW heat pack on the 3T unit. So I'm not sure this is the source of my overall energy use reporting issue. Anyone run into this issue previously or can confirm the installed location of their fan CT for 3T or 4T units with or without heat packs?