We purchased this home in 2009 with a Water Furnace E-Series GEO Thermal heating and cooling sytem. In Febuary of 2010 we had no heat, called the installer and they came out and checked the system and got it working at a service charge of $444.00. The repair, what ever it was lasted a few days because they were back again on March 1 2010. At this time they found the thermostat and control board were faulty and replaced under warranty. The parts were: Water Furnace Logic Board 17P513-03 and Water Furnace W/R 90 Series Blue 1F95-1271 TP32W02. This unit failed again on 12/27/2011. At this time the unit needed a leaking evaporator coil and a bad compressor in the E048TR111NBDSSA Serial # WF2295 replaced. At this time they replaced the compressor with : Compressor conversion kit E 048 Bristol Twin Single to a Copeland Scroll W/Control Board BSCK048, Water Furnace Bi-Flo Filter-Drier 3/8 BFK-083S36P500B01, Water Furnace Evaporator Coil 61S539C02. All of these parts were covered under warranty, but all the labor was not. Labor costs were $1,100.00 The unit worked very well until 02/28/2014 at which time we had no heat again. This time we needed a Blower Fan Motor replaced. On 03/03/2014 the blower was replaced with a, Water Furnace ECM Blower Fan Motor 1/2 HP, 208/230 V-14P516B01 and again covered under warranty except for $278.20 in labor. The unit worked well again for one year, and on 03/19/2015, no heat. This time a bad capicator was found and a new Motor Run Capacitor was replaced. No warranty on this and the cost was $274.99. Again, the unit worked well until 12/27/2018. On this day we woke up to no heat and called the repair company. I am not using any names but we have used the same company to repair this unit that installed it. The repair men came out and informed us that our furnace needed a compressor again. They did not have the part nor could they give me an estimate on repair costs because according to them the Water Furnace Company warehouse was closed until after the New Year. So we have been using the emergency electric heat in our home while waiting for an estimate from the repair company. After no word from the repair company I phoned them on 01/07/2019 and left a message. The next day I got an e-mail estimate to replace the compressor with labor for a price of $3,567.67. Almost every part of this Water Furnace E-Series has been replaced and now after only 7 years the compressor needs replacing again. I would like some advice or insight as to what others would do with this furnace. My wife is at the point where she would like to have the unit removed and a gas furnace installed in it's place, me I am just angry!