I have a hydronic heat pump going in High Pressure lockout. The dealer told me to close 50% the in and out valves on the ground side. Doing so the pump is running, but I think is not the solution. In the manufacturer manual for HP lockout are 2 possbility: overcharged with refrigerant, or malfunction of Expansion valve and sensing bulb. Could someone help me in solving the problem?